Water management is the most vital aspect today. Technically there should be an aim to efficiently manage water problems. This article focuses on the introduction of new control system for the municipal water district of normal, illinois that has brought in more effeciency. Lets read on and find out about the new control system through this article.
Because of the introduction of this new control system it has increased skilfulness and it has lessened the burden of maintainance to a considerable extent. This is the proof that till today the Normal, Illionis water system has been running smoothly. Earlier the employees of the Normal Water Department were struggling hard to fulfil the needs of the consumers. The system initially was a bit complicated one to understand which contained the reflection of outdatedness. The system gave multiple problems. The control system is much more convenient and flexible with great potentials. A new control system for the municipal water district of Normal, Illinois brought in more efficiency and lightened the burden of maintenance. License-free wireless radios were installed, increasing data transmission from 300 bits per second to 57,600 bits per second. The Normal, Illinois water system has been up and running successfully since December 2002. In Normal, Illinois, housing a population of 46,000 and home to Illinois State University, the 28 employees of the Normal water department were scrambling to meet the needs of their consumers. The treatment divisions responsibilities included the operation and maintenance of 14 wells, a lime softening treatment plant, three booster pumping stations, four elevated tanks and one ground storage reservoir. The distribution division was charged with operating and maintaining 170 miles of water mains, reading and maintaining more than 13,000 services and the installation and repair of water mains, valves and hydrants. All of this furious activity was being accomplished with an outdated system containing remote terminal units (RTUs), which performed only minimal SCADA and licensed-frequency radios, which sent data at a mere 300 bits per second. Overall the system was complicated to understand, expensive to service, and difficult to repair.
Normal Water turned to SCADAware - a system integration firm in nearby Bloomington - expressing their desire for a new system, built from the ground up. In an effort to control costs and allow Normal to create, install, maintain and repair its new system with minimal outside help, Rick Caldwell, president, SCADAware, recommended a PC-driven, license-free, frequency hopping spread spectrum solution. Normals new system now uses a primary and secondary server within its water treatment plant for HMI, and PC-based control. The computers collect and monitor data from all of Normals wells, tanks and lift stations via a ProSoft Technology wireless serial network, with data rates of 57,600 bits per second. Programmable field couplers allow water treatment personnel to make adjustments and activate controls. A SIXNET Ethernet-to-Serial is used to convert the incoming serial data to Ethernet, allowing the data to be accessed on the plants LAN. "The monitoring of wells and tanks using the wireless network cuts down on drive time and time away from the department," said Jim Weikert, RadioLinx manager, ProSoft Technology. "The sophisticated software alerts water department employees of problems, reducing response times."
Although justifying upgrades of this nature can be very challenging for municipal departments, the team at Normal felt that this upgrade would have an immediate, positive economic impact on performance and efficiency. They were right.
"The easily administered SCADA system and the wireless network allowed Normal to have the flexibility to upgrade and change their system as the need arises," said Kevin Zamzow, RadioLinx Engineer, ProSoft Technology. "Future expansion has now become more affordable for the Normal, Illinois water department. The present solution has also become much more efficient and less burdensome to maintain." The Normal, Illinois water system has been up and running successfully since December, 2002.
|Posted : 10/21/2005|